Active Fire Prevention with OxyReduct® in Paper Roll Warehouse
WAGNER protects the newly built paper roll warehouse of Paloma AG in Sladki Vrh, Slovenia, from fires. The new warehouse building went into operation in March 2021. The fully automated high-bay warehouse for hygiene paper is effectively protected with a combination of active fire prevention and early fire detection using air sampling smoke detectors.
Paloma produces so-called jumbo rolls at its headquarters. These are processed into toilet paper, kitchen towels, napkins, handkerchiefs and universal towels for industrial and medical use, as well as into maxi rolls. Due to its properties, paper is light and highly combustible. A comprehensive fire protection solution is therefore a must.
The fully automated high-bay warehouse has a volume of 38,000 cubic meters with a height of 21 meters. It is connected to production via an airlock. The basic product for handkerchiefs, toilet paper and kitchen rolls is stored there. The so-called jumbo rolls have a considerable size with a diameter of up to 2.5 meters and a maximum height of 2.75 meters. The density is 180 to 225 kg/cubic meter. Due to these dimensions, the jumbo rolls are stored directly on the floor and a maximum of two rolls are stacked on top of each other.
Paloma has more than 140 years of tradition in the production and marketing of sanitary paper products in Europe and is the market leader in Southeast Europe. The producer exports and produces about 72,000 tons of hygienic paper per year. Paloma is also part of the Slovak Hygienic Paper (SHP) Group, which is the largest producer of hygienic paper for Central and Eastern Europe.
Maintaining Product Availability, Protecting Products in the Best Possible Way
Rolls sprayed with sprinkler water can no longer be moved and become 100% unusable. Water-based extinguishing agents are therefore not an option.
The Solution for Paloma's Paper Roll Store is Called Active Fire Prevention
The fire protection solution for Paloma is based on the principle of active fire prevention. The risk of an open fire with direct and corresponding consequential damage can thus be reduced. The solution designed and implemented by WAGNER consists of the OxyReduct® oxygen reduction system and an early fire detection system with TITANUS® air sampling smoke detectors, which have a particularly high sensitivity.
Planning and construction of the system complies with EN 16750. In order to determine the oxygen level for active fire prevention, fire tests were also carried out together with the customer at WAGNER's headquarters in Langenhagen. The result is a low ignition limit, so that the protected area may not be entered without additional measures.
The fire protection technology is housed in a separate technical room directly adjoining to the warehouse.
WAGNER's fire protection solution provides comprehensive protection for the new warehouse building.
More Impressions of Paloma
If you need advice on a suitable fire protection solution, want to comprehensively protect a new warehouse or have any other need for one of our fire protection solutions, please feel free to contact us. We will arrange a personal consultation appointment with you.